As an Amazon Associate, we earn from qualifying purchases. This does not affect the price you pay or the quality of the products you buy. For more information, please read the full affiliate disclosure here.
Imagine you’re in the middle of a power outage, and you need to use your diesel generator to keep your appliances running. You plug in your fridge, your TV, your laptop, and your phone charger. You turn on the generator and wait for the power to come on.
But something is wrong. The lights are dim, the TV is fuzzy, the laptop is slow, and the phone is barely charging. You check the voltage output of the generator and see that it’s way below the normal level. What’s going on?
You’re experiencing low voltage output, a frustrating and annoying problem that affects many diesel generators. Low voltage output means that the generator is not producing enough electrical power to meet the demand of the load. This can cause overheating, damage, or malfunction of the equipment.
If you have a diesel generator, you may have encountered this problem before, or you may want to prevent it from happening in the future. How do you fix this problem? What can you do to prevent it from happening again?
In this blog post, we will explain some of the most common causes and solutions for the low voltage output of diesel generators.
More articles on generator hacks that may help you with your diesel generator low voltage output issues.
- Generator Running Under Voltage Fault Troubleshooting Guide
- How to Reduce Voltage in a Generator in 4 Simple Ways
- How to Adjust Generator Voltage: A Step-by-Step Guide
- Generator Output Voltage Too High: A Troubleshooting Guide
- How to Fix a Low Voltage Generator in 3 Easy Ways
8 Causes of Diesel Generator Low Voltage Output and Their Solutions
Reason 1: The generator is overloaded.
One of the simplest and most common reasons for low voltage output is that the generator is overloaded. This means that the load connected to the generator is greater than its rated capacity. When this happens, the generator cannot maintain its speed and frequency, and the voltage drops.
The solution to this problem is to reduce the load on the generator. You can do this by disconnecting some of the devices or appliances that are not essential or by using a larger generator that can handle the load. You can also use a load meter or a wattmeter to monitor the load on the generator and avoid overloading it.
Reason 2: A Faulty Circuit Breaker
Another possible cause of low voltage output is a faulty circuit breaker. A circuit breaker is a device that protects the generator and the connected devices from overcurrent or short circuits.
It automatically shuts off the power when the current exceeds a certain limit. However, sometimes the circuit breaker may trip or malfunction due to wear and tear, dirt, moisture, or other factors. This can result in low or no voltage output from the generator.
To fix this problem, you need to check the circuit breaker and see if it is in the correct position. If it is tripped, you need to reset it by switching it off and on. If it is damaged or faulty, you need to replace it with a new one.
You can also use a multimeter to measure the resistance of the circuit breaker and the wiring connections. If the resistance is too high or too low, it indicates a problem with the circuit breaker or the wiring.
Reason 3. Loose or Corroded Connections
Another common cause of low voltage output is loose or corroded connections. The connections between the generator and the load, between the generator and the battery, or between the generator and the ground can become loose or corroded over time. This can increase the resistance and reduce the current flow, resulting in low voltage output.
To fix this problem, you need to inspect the connections and make sure they are tight and clean. You can use a wire brush or sandpaper to remove any rust or corrosion from the terminals and the wires.
You can also use a contact cleaner or dielectric grease to protect the connections from moisture and dirt. You should also check the cables and wires for any cracks, cuts, or damages and replace them if necessary.
Reason 4: Faulty AVR or Capacitor
Another possible cause of low voltage output is a faulty AVR or capacitor. AVR stands for automatic voltage regulator, and it is a device that controls the voltage output of the generator by adjusting the excitation current of the alternator.
A capacitor is a device that stores electrical charge and helps stabilize the voltage output of the generator. Both of these devices can fail or deteriorate due to age, heat, moisture, or other factors. This can affect the voltage regulation and output of the generator.
To fix this problem, you need to check the AVR or the capacitor and see if they are working properly. You can use a multimeter to measure the voltage output of the generator and compare it with the rated voltage. If the voltage is too low or too high, it indicates a problem with the AVR or the capacitor.
After that, use a multimeter to measure the resistance or capacitance of the AVR or the capacitor. If the resistance or the capacitance is too low or too high, it indicates a problem with the AVR or the capacitor. You need to replace the faulty AVR or capacitor with a new one.
Reason 5. Mechanical Malfunction
Another possible cause of low voltage output is mechanical. The mechanical parts of the generator, such as the engine, the fuel system, the air filter, the oil filter, the turbocharger, etc., can affect the speed and the power output of the generator.
If the engine speed is unstable, the voltage output will also be unstable. This can be caused by problems with the fuel system, the governor, the air intake, the exhaust, or the cooling system.
If any of the parts mentioned are damaged, dirty, clogged, or worn out, they can reduce the efficiency and performance of the generator.
To fix this problem, you need to check the mechanical and alternator parts of the generator and see if they are in good condition.
You need to perform regular maintenance and service on the generator, such as changing the oil, the fuel, the air filter, the oil filter, the governor, etc.
You also need to clean and lubricate the moving parts of the generator, such as the engine, the turbocharger, etc.
Reason 6: Problem with the Alternator
A problem with the alternator stator can also cause low voltage output in diesel generators. The stator is the stationary part of the alternator that contains the field coil or the armature coil, depending on the type of alternator.
There are two types of alternators:
- and brushed.
A brushless alternator uses two sets of rotors that spin together to generate and transfer the electrical current, while a brushed alternator uses carbon brushes to help conduct electricity.
A brushless alternator has many advantages over a brushed alternator, such as higher efficiency, longer life, lower maintenance, and a smaller size.
To fix a problem with the alternator, you need to check the condition and see if it is damaged or worn out. You can use a multimeter to measure the resistance or the voltage and compare it with the specifications.
If the resistance or the voltage is too low or too high, it indicates a problem. You need to replace it with a new one. You can also use a visual inspection to look for any signs of damage, such as cracks, burns, or corrosion, that may affect the performance of the alternator.
Reason 7: Problems with the Stator
The stator is the stationary part of the alternator that contains the coils that generate the voltage. If there is a short circuit or a ground fault in the stator winding or the excitation winding, the voltage output will be reduced. This is because the fault reduces the effective resistance of the winding, which lowers the induced voltage.
To check and clear the fault, you need to disconnect the generator from the load and the power source and use a multimeter or a megger to measure the resistance and insulation of the windings. If the resistance is too low or the insulation is too poor, it indicates a fault in the winding. You need to locate and repair the fault, or replace the winding if necessary.
Reason 8: Faulty Rectifier Diodes
The rectifier diodes are responsible for converting the alternating current (AC) from the alternator to direct current (DC) for the excitation circuit. If some of the diodes are broken or damaged, they can cause distortion or a reduction in the output voltage.
Some rectifier diodes may be broken down, meaning that they have lost their ability to block the reverse current and allow current to flow in both directions. This can result in a distorted or reduced output voltage and damage the generator or the load.
To deal with this problem, you need to identify and replace the broken diodes. You can use a multimeter to test the diodes by measuring the forward and reverse resistance. If the resistance is too low or too high in both directions, it indicates a broken diode.
You can also use a visual inspection to look for any signs of physical damage, such as cracks, burns, or melting. You need to replace the broken diodes with new ones with the same specifications.
Frequently Asked Questions
What are the effects of low-voltage output on appliances?
Low voltage output can cause overheating, damage, or malfunction of the appliances connected to the generator. It can also reduce the efficiency and lifespan of the appliances. Therefore, it is important to monitor the voltage output of the generator and avoid overloading it.
How do you test for low voltage in a generator?
You can use a multimeter to measure the voltage output of the generator and compare it with the rated voltage. If the voltage is too low or too high, it indicates a problem with the generator. You can also use a load meter or a wattmeter to measure the load on the generator and avoid overloading it.
Is it costly to repair a generator with a low voltage?
The cost of repairing a generator with low voltage depends on the cause and extent of the problem. Some problems, such as overloaded generators, loose connections, or faulty circuit breakers, can be fixed easily and cheaply by reducing the load, tightening the connections, or resetting or replacing the breaker. Other problems, such as a faulty AVR, capacitor, stator, or alternator, may require more professional and expensive repairs or replacements.
Can bad ground cause low voltage?
Yes, bad ground can cause low voltage in a generator. A bad ground means that the generator is not properly connected to the earth, which can affect the stability and safety of the voltage output.
Bad ground can also increase the risk of electric shock or fire. To fix this problem, you need to check the ground wire and the ground rod of the generator and make sure they are in good condition and securely attached.
Low voltage output of generators can be caused by various factors, and it can affect the performance and safety of the connected devices.
To fix this problem, you need to identify the cause and apply the appropriate solution. You also need to monitor the voltage output of the generator and avoid overloading it.
You also need to perform regular maintenance and service on the generator to keep it in optimal condition. By following these tips, you can ensure that your diesel generator provides reliable and efficient power for your needs.